I’ve never seen this setup. It is a standard Armstrong Ultra SX Cat 1 furnace. The installation is in the crawl space, with a horizontal vent out the side of the wall. There is a booster fan at the vent termination that is wired into the inducer fan circuit. Seems to be working fine, but I have my doubts that the manufacturer would approve of the installation. Any thoughts? I couldn’t find any info on the Allied or Armstrong web sites that was helpful.
***IMPORTANT*** You Need To Register To View Images 0110.jpg